See all Canadian Tire Questions and Answers >
Home Q & A >
Heating & Air Conditioning Q & A >
Baseboard & Wall Heaters Q & A

Garrison Garrison Convection Heater

Available in 500W, 1000W, 1500W and 2000W for fast radiant heatQuiet operation ideal for sleeping and living room areas and simple fade resistant design that suits any dÃ©corStainless steel element with sheathCompatible with any line voltage thermostat500W heating capacity is recommended for rooms u

Question

In the description it says this product is compatible with any line voltage thermostat...I would like to know if there is actually a thermostat built into this heater?

asked 7 years, 7 months ago on Garrison Convection Heater

by

Anonymous

- Timmins

2 answers

Answers

answer 1

No.

answered 7 years, 6 months ago

by

hilsenteger

answer 2

On these models they do not have a built in thermostat.

answered 7 years, 7 months ago

by

Greg

Question

This will replace any standard baseboard heating system? As well do this required any special installation (a Master electrician is need it) or can be done easily.

asked 7 years, 6 months ago on Garrison Convection Heater

by

Anonymous

2 answers

Answers

answer 1

An licensed electrician is required to do ANY electrical work in your home. If your house burns and your insurance company finds out you did your own electrical work, they will not honor your claim.

answered 4 years, 4 months ago

by

Anonymous

answer 2

Your standard baseboard must be at 240v if you want to replace it with this item.

There should be two wires, a black and red, or black and white wire, plus ground. Just simply replace the existing baseboard with this product using the exact same connections.

Make sure power is turned off before doing any electrical work.

There should be two wires, a black and red, or black and white wire, plus ground. Just simply replace the existing baseboard with this product using the exact same connections.

Make sure power is turned off before doing any electrical work.

answered 6 years, 3 months ago

by

tony128

- Vancouver

Question

I am not too impressed by the lack of availability of spec info and installation instructions. Most products have this available on-line. I can't even find a manufacturers site for NOMA heaters. Is it possible for you to make this available?

asked 7 years, 5 months ago on Garrison Convection Heater

by

Anonymous

2 answers

Answers

answer 1

After calling the manufacturer their staff was unable to answer basic questions such as 'How hot does the surface get - I want to place the heater in my childrens room.' I got hung up on when I asked, 'Has the heater been tested for an energy star rating, what would it cost to run the heater on an average daily basis?' If you call be prepared to give your personal phone number before they will answer anything. Call 800-459-4409 to see if you have better luck.

answered 6 years, 3 months ago

by

LivMom

answer 2

I was checking in to this product as well. This is what I found out. It's made by Quality Craft Home Decor and here is their site directly to the heater:

http://www.qualitycraft.com/products/homedecor/convectionheaters/qcc1000

It has a manual there that may be able to answer any of your questions. Good luck.

http://www.qualitycraft.com/products/homedecor/convectionheaters/qcc1000

It has a manual there that may be able to answer any of your questions. Good luck.

answered 6 years, 7 months ago

by

Girlplaty

- PEI

Question

asked 6 years, 6 months ago on Garrison Convection Heater

by

Anonymous

- toronto

2 answers

Answers

answer 1

It is impossible for electrical heaters to be efficient. A watt is a unit of energy over time. An analogy would be to set your thermostat to 15 degrees and expect your room to warm up to 20 degrees.

The term "energy efficient", as we know it, primarily means that manufacturers have be able to reduce the amount of wasted energy for a motor, and most energy is wasted as either noise or heat.

Since electric heaters have no motor, if you put in 1000 watts of energy, you will get out 1000 watts of heat. There is no way to only put in 500 watts of energy and get out 1000 watts of heat

The term "energy efficient", as we know it, primarily means that manufacturers have be able to reduce the amount of wasted energy for a motor, and most energy is wasted as either noise or heat.

Since electric heaters have no motor, if you put in 1000 watts of energy, you will get out 1000 watts of heat. There is no way to only put in 500 watts of energy and get out 1000 watts of heat

answered 6 years, 2 months ago

by

Frankaroo

- Montreal

answer 2

all electric heaters are 100% efficient baseboard ,convection e.t.c

answered 6 years, 6 months ago

by

ruttger

Question

The manual online warns that it gets hot and not to leave children unattended. I want this for my daughter's playroom...is it safe for that? Anyone know how hot it gets (in general terms)?

asked 6 years, 3 months ago on Garrison Convection Heater

by

Anonymous

2 answers

Answers

answer 1

We have a 1000W and the reading I got off my infrared laser is about 70C at the top. air coming out is warmer then that...

answered 5 years, 4 months ago

by

Anonymous

answer 2

The unit gets hot like any other electrical heater (baseboard or convector). It is always best to be cautious when operating.

answered 6 years, 2 months ago

by

MeredithTO

Question

Does anyone know if this unit will run on 110 volts?

asked 6 years, 2 months ago on Garrison Convection Heater

by

gcoleman

- North Vancouver

2 answers

Answers

answer 1

These heaters will run on 110 volts, but you will only get 25% of the rated heat. A 2000 watt heater rated at 220 volts will produce 500 watts of heat at 110 volts. Half the voltage will produce half the current, therefore we get:

voltage x current = watts

.5 voltage x .5 current = .25 watts.

500 watts x .25 = 125 watts.

voltage x current = watts

.5 voltage x .5 current = .25 watts.

500 watts x .25 = 125 watts.

answered 5 years, 5 months ago

by

Anonymous

answer 2

No this heater will only run on 240 volts. And it must be hard-wired.

answered 5 years, 7 months ago

by

Anonymous

- Kitimat, BC

Question

I replace an existing baseboard heater, Have a new thermostat, tested voltage and have 120 on black wire and 120 on white for a combined 240 . Have verified that power is on however no heat.

asked 6 years ago on Garrison Convection Heater

by

Anonymous

2 answers

Answers

answer 1

Did you check the temperature breaker for continuity. Mine worked good for a year then this little switch on the inside back of the heater has failed and I can't find where to replace it. I was told you can't buy repair parts I should just discard it and buy a new one.I can jumper it out but too dangerous to leave it that way. 2000 watts

Ray

Ray

answered 5 years, 4 months ago

by

Anonymous

answer 2

Measure the to see if there is an element resistance.

R- V^2/P = 115.2 ohms for 500 watt heater.

R- 28.8 ohms for 2000 watt heater. (more or less).

R- V^2/P = 115.2 ohms for 500 watt heater.

R- 28.8 ohms for 2000 watt heater. (more or less).

answered 5 years, 4 months ago

by

Anonymous

Question

asked 5 years, 4 months ago on Garrison Convection Heater

by

Chateaumau

- Winnipeg

2 answers

Answers

answer 1

it can be used on a 15 or 20 amp breaker

answered 5 years, 2 months ago

by

Anonymous

answer 2

No more than a standard baseboard. If you are replacing an existing Baseboard for this, make sure you use one with the same wattage.

If you are replacing for a higher wattage, make sure you are not going over the brakers capacity.

Watts = Voltage X Amps

To know how many watts you should use in a room. In a well insulated room for electric heat:

calculating the width X length X height X 1.5 divided by 250 watts per foot of heater. This will tell you the minimum heat required to heat that room.

On regular baseboard, calculate watts of the heater multiply the number of feet long the heater is times 250 watts per foot to find watts of that heater.

To calculate how many watts you may put on a 20 amp 240 volt branch circuit.

Typically, you would be able to install 4800 watts per 20 amp branch circuit @ 100%. I advise not to exceed 80 % load on each 20 amp branch circuit.

If you are replacing for a higher wattage, make sure you are not going over the brakers capacity.

Watts = Voltage X Amps

To know how many watts you should use in a room. In a well insulated room for electric heat:

calculating the width X length X height X 1.5 divided by 250 watts per foot of heater. This will tell you the minimum heat required to heat that room.

On regular baseboard, calculate watts of the heater multiply the number of feet long the heater is times 250 watts per foot to find watts of that heater.

To calculate how many watts you may put on a 20 amp 240 volt branch circuit.

Typically, you would be able to install 4800 watts per 20 amp branch circuit @ 100%. I advise not to exceed 80 % load on each 20 amp branch circuit.

answered 5 years, 4 months ago

by

rmarier

- Laval, QC

Question

I connected it to the 110V power supplie but it's giving quarter the heat it''s supposed to give. how can i choose a transpormer that can support this 1000w unit?

asked 4 years, 6 months ago on Garrison Convection Heater

by

leeroy514

- Montreal

2 answers

Answers

answer 1

The convection needs a power supply of 240V/60Hz and will require a certified electrician to install it. Do not connect the 110V power supply directly. Use the transformer which the electric current exceeds 15Amp.

answered 4 years, 5 months ago

by

liz6432

answer 2

This is because you have to connect it to 240V. You will probably need to install a new breaker and wires from the breaker to the unit. You should ask an electrician to do the installation.

answered 4 years, 6 months ago

by

Anonymous

Question

I was wondering the hieght,width&lenght of heaters?

asked 7 years, 6 months ago on Garrison Convection Heater

by

skidoo

- k.lake

1 answer

Answers

answer 1

The dimensions are 17.44" (44.3cm) high, 22.87" (58 cm) long and 4" (10.2 cm) wide.

answered 6 years, 11 months ago

by

alex2052

- toronto